Check out our latest round-up of #CaughtOnCamera shockers! Have you seen something shocking, funny or surprising while on the job? Take a pic and send it in via DM on one of our social channels or send it directly to [email protected] for the chance to be featured!
We’re back with another #caughtoncamera ! This one was sent in by Mike Bowles “Doing a visual inspection at the start of an EICR and found the electric shower shown on the consumer unit in the ensuite bathroom. It was a 600mm square shower cubicle with the 45A double pole isolator inside the shower cubicle.. It got better – the electric shower was an 8.5kW unit, fed on a 40A mcb, however the cable was only 4mm twin & earth. Needless to say I decommissioned it immediately. The tenant wasn’t very happy!”
Check out this dangerous #caughtoncamera sent over by Richard Marshall “I removed a metal light fitting while carrying out an EICR and found this beauty! Yes, that’s a permanent live in a bare terminal bar from a ceiling rose!”
A shocking #caughtoncamera we received recently from Robert Keighery – “I went to carry out an EICR and found this wonderful bit of so called “genius” – a lighting circuit adapted to feed a surge protected extension lead with all the lighting circuits now on a plug top. It turns out the customer had issues with the bulbs blowing, so someone thought this might solve the problem!”
For lighting, electrical, signage, and technology solutions that allow you to do more call Sverige Energy today at +4(670) 4122522.